The Te Mato Vai Project to update Rarotonga’s intakes and water main includes implementation of a 4-stage treatment process. Chemicals have been proposed for Stage 2: Coagulation/Flocculation to remove fine particles; and Stage 4: Water Disinfection to kill or inactivate micro-organisms.
Polyaluminum chloride (PACl) has been proposed to improve water clarity (turbidity). When added to the source water, the chemical causes smaller particles to clump together; these clumps then fall to the bottom of a settlement tank or are removed by subsequent filtration methods.
Disinfection requires that water is clear. Particles in clouded water can prevent the disinfection from deactivating potentially harmful micro-organisms. Clear water improves the effectiveness of disinfection: whether the disinfection method is chemical (e.g. chlorine solution); or physical (e.g. UV irradiation).
Adding a coagulation chemical is one method of treating water to improve clarity. There are alternative physical (non-chemical) treatment methods that can also be used to improve clarity, such as not collecting water in high-turbidity conditions (diversion); centrifugal separation; passing water over a electrical plate; or use of fine filtration.
Stage 4 Disinfection: Calcium Hypochlorite
Although the Cook Islands Government has continued to issue the statment that ‘No decision has been made on disinfection’; chlorine solution storage and dosing equipment was ordered in 2018 and installed by contractors at each of the ten intakes from early 2019; prior to the community presentation and discussion of disinfection options in May 2019.
The Cook Islands National Water Policy (2016)“[brings] together government policies for water resources management, infrastructure, water supply, drinking-water safety planning and sanitation.”
This document makes a number of references to water management and environmental considerations that apply to the Te Mato Vai Project and the operations of the new water authority To Tatou Vai.
Taking active measure to prevent serious or irreversible environmental damage or degradation whether the consequences are uncertain or not.
Sustainability & Environmental preservation
Strive to protect and avoid adverse interference with the natural ecology of the Cook Islands’ waters and lagoons and ensure that usage and management of water will be conducted in a manner that will preserve and enhance this resource for generations to come.
Mitigation of the impact of Infrastructure and Development on Ecological Flows In designing and delivering future water supplies, infrastructure, services and operations will be provided in a manner that ensures that ecological flows are maintained in natural streams and waterways to the greatest extent practicable in order to ensure the protection of freshwater and coastal ecosystems.
Cook Islands National Water Policy
Environment Act 2003 / Te Mato Vai Stage 2 Environment Impact Assessment
Groundworks and construction in areas of specific concern are subject to regulation in the Cook Islands under the Cook Islands Environment Act 2003; areas of concern include sloping lands and sites in close proximity to waterways/streams. The new Te Mato Vai water treatment plants are located in such areas.
Before construction can commence, the applicant may be required to complete a report detailing possible environmental impacts of the project and the measures and monitoring that will be taken to minimise such impacts. The resulting Environment Impact Assessment (EIA) report must be made available for public consultation to allow for formal community and stakeholder response.
An example water treatment process schematic diagram include a note that a “Flocculating Agent may be injected (if required) to aid removal of finer particles”; however no detail is provided regarding the construction or operation of a specific chemical treatment system.
3.1.2 Water Treatment Upgrade (schematic), Te Mato Vai Detailed Design for Stage 2, Draft Environmental Impact Assessment Report. GHD, August 2015 Accompanying caption: Figure 3 - Indicative flow diagram to illustrate how the proposed gravity operated water supply and treated system works.
With the project now nearing completion, it can now be seen that ommitting detail from the EIA report has prevented the public from raising concerns about the treatment method (prior to the commencement of the construction project), and is a likely violation of the intended consultation and approval process.
2015 Construction EIA: Nature conservation
The construction EIA report stressed that the constractors should take steps to prevent the accidental discharge of wastes: excess soil, vegetation, sanitary waste, and machinery fluids. The report also proposed conditions for activities that had the potential for (unintended) impact on the stream.
Contractors are expected to prepare an Erosion and Sediment Control Plan as
part of the [Construction Management Plan] for approval by NES [to] assist in minimizing the anticipated effects of these activities. Activities that have the potential to impact on stream conditions must avoided during the full moon days (three days before and after the full moon), the spawning times for koura or Macrobrachium.
-Te Mato Vai Stage 2 Construction EIA Report. GHD, 2015.
Expert Review / March 2020: ‘Risks to freshwater ecology…’
An Expert Review, commissioned by the Cook Islands Ministry of Justice, confirms that the Stage 2 Permit, does not cover the operational use of chemicals. The proposed PACl trial is the operational use of chemicals.
There will be an aluminium residual in the supernatant discharged from the ponds to the streams. The EIA for TMV Stage 2 was prepared in the very early stages of design (2014) and, although a schematic of the treatment process mentions that “Flocculating agent may be injected (if required) to aid removal of finer particles”, the assessment ignores the potential impacts of using flocculant chemicals on the environment. The Mott MacDonald Detailed Design Report does not cover any environmental impacts.…
Given the number of unknowns in the above, and I suspect the rather unique freshwater ecology of the streams of Rarotonga, I think the recent ecological report study (referred to in Mr. Free’s letter to me dated 4 March) should be circulated to the parties. Other non-aluminium coagulants could be considered as this would eliminate the risks from aluminium to the freshwater ecology.… -Te Mato Vai - Stage 2 - Expert Independent Review. Ministry of Justice. March 2020.
Above: Pipes leaking into the Turangi stream, approx 100m from the water treatment plant. June 6 2019.
Turangi Pipe-leak Updates
19 July 2019: The above blue-collar thermo-coupling has been repaired. The older asbestos concrete (AC) pipe length is still leaking. In drought conditions, water leaking from the trunk main is the only water entering this part of the Turangi stream. The PMU have indicated that this length of pipe may be decommissioned when the new system is made live.
4 Sept 2019: Te Mato Vai have advised that the pipework that spans the streams will be the final sections of pipework to be replaced. The above ground pipework will be fibre-coated metal rather than the softer high-density uPVC plastic used for the in-ground network. The weight and vibration of water moving through the pipes require the strong metal pipes to be used. In-ground pipes are bedded in sand.
4 Dec 2019: Still leaking. Along with chlorine; dissolved aluminium and PACl sludge is also toxic to aquatic life. The operation of the new Te Mato Vai system proposes regular discharge into the stream of supernatant (PACl wastewater); and onsite storage of PACl sludge, before transfer to the Arorangi landfill. See: PACl on Trial.
22 Apr 2020: Road closure and work underway on new trunkline. Construction of a (temporary?) upstream dam and excavation suggesting the new trunkmain may run underneath the ford.
5 Aug 2020: After heavy rains, the corroded pipe snapped, as did a the the Avana trunk line. Te Mato Vai have been forced to switch over to the new system. (Public advised via Facebook post 14 Aug 2020.)
Network failure will result in chemically-treated water contaminating waterways as pipework often follows the stream route out of the valleys.
Freshwater aquatic life is highly sensitive to chemicals, with acute toxicity to chlorine at very low dosage.
Active chlorine is toxic to fish from levels as low as 4 parts chlorine to 100,000,000 parts water. In periods of low waterflow/drought, leakage from the water main may be the only water in the streambed (below the intake point).
Active chlorine is very toxic to fish. Its toxicity largely depends on water
temperature: for example, an active chlorine concentration of 3.5 mg per litre has a sublethal effect on carp at a water temperature of 3–7°C but when exposed to the same concentration at a temperature of 15–20°C they die in 1 to 2 hours. In general, a prolonged exposure to active chlorine concentrations of 0.04 to 0.2 mg per litre is considered to be toxic to the majority of fish species. (PDF) Water Quality and Fish Health, United Nations FA0 (1997)
WHO Drinking-Water Standards for Chlorinated Supply
The WHO standard for residual chlorine disinfection is 0.2-5 mg/L. At this level water ‘from the tap’ will be toxic to the majority of fish species. Leakage nearer the intakes will be more toxic due to the higher levels of active chlorine.
What will the chlorine level be as water enters the network?
WHO recommends that the concentration of active chlorine in water entering the network to be at least 0.5mg/L and no greater than 5mg/L. (The concentration of chlorine in pool water is 2-4ppm).
Commissioning: Super-chlorination Disinfection
Prior to the new Te Mato Vai system being made ‘live’ the network pipes and plant (including storage tanks) are required to be disinfected, using a ‘shock’- or super-chlorinated solution. This is to remove any construction waste and disinfect surfaces that might pose a health-hazard to the public.
When instructed to do so by the Engineer, the Contractor shall disinfect the pipeline by chlorination either in sections or as a whole. The Contractor shall provide a suitable chlorine dose pump and chlorine which is capable of accurately injecting the required concentration of chlorine solution at steady rate into the pipeline.
The Contractor shall introduce at least 20ppm of chlorine or such greater quantity of chlorine as will produce a residual of at least 1ppm of free chlorine at any point along the pipeline being sterilised 2 hours after the section of pipeline has been filled with water.
If after 24 hours, the residual chlorine is 1ppm or greater, then disinfection shall be deemed to be complete and the chlorinated water shall be drained and flushed away to a suitable outlet where no harm will result from the flow or its contents. Dispose of disinfected wastewater to meet relevant Regulation and ICI Requirements.…
-Infrastructure Cook Islands Technical Standards for Water Supply in Partnership with the Institution of Professional Engineers Cook Islands, 30 May 2014
Specific chlorine dosage values from standard-to-standard, but in New Zealand can reach starting levels of up to 100mg/L (prior to neutralisation). Even when reduced to the recommended disposal dosage of 1ppm, this is still 25 × the level at which the chemical is toxic to freshwater aquatic life.
Along with the connecting pipework, commissioning includes the sterilisation of the new 1.8–2.3 million litre water storage tanks (some intakes have two such tanks). Given the remote inland locations (lacking a suitable outlet for disposal); logistics of removing the wastewater, sterilisation water will be discharged either into the ground or into the intake valley streams.
The coagulant chemical polyaluminum chloride (PACl) is proposed to remove sediment and fine particles from source water.
Aluminium in the aquatic environment can have a major impact on aquatic life. Acid precipitation [acid rain] has been implicated in the loss of fish populations from acid sensitive waters through the mobilisation of aluminium… The short-term changes in aluminium concentrations caused by these events can have severe effects on aquatic biota. Canadian Water Quality Guidelines for the Protection of Aquatic Life: Aluminium. Candian Council of Ministers for the Environment, 2003 (Withdrawn).
In the Cook Islands, infrastructure projecs in areas of specific (environmental) concern are required to complete an environmental impact assessment process. This includes public consultation processes. Despite initially claiming that the necessary regulatory processes had been completed, in January 2020 a release was issued through the Te Mato Vai Facebook Page (later attributed to the new water authority - To Tatou Vai), that a stream survey was to be undertaken as part of an EIA into the operational use of PACl. The stream survey was conducted over a 1-2 week period in January 2020 by government consultants GHD (pers. comm. To Tatou Vai).
Although better-late-than-never, a two-week spot sample may be insufficient given that operation of the new system proposes to decant dissolved aluminium wastewater into the freshwater streams (also noting the companion risk of unintended overflow of the sludge storage ponds).
Conditions of pH, total hardness and dissolved organic carbon (DOC) may vary within a waterbody throughout the year, thereby affecting the bioavailability of aluminum over time. To ensure the criteria will be protective during the times when aluminum is most bioavailable (and most toxic), the EPA recommends that the state or authorized tribe collect, if possible, 24 months of monthly sampling data for the three input parameters. This approach will help to account for both intra- and inter-annual variability of the input parameters.
Implementing the 2018 Recommended Aquatic Life Water Quality Criteria for Aluminum. United States Environmental Protection Agency (EPA).
Freshwater impacts - alum application
Dissolved aluminium bonds with phosphorous and can be used to remove excess amount of this nutrient from freshwater systems, chiefly lakes that are negative affected by excess fertiliser run-off.
The practise of dosing with alum (aluminiuim sulphate), has led to renewed interest in the long-term impacts of aluminium on freshwater ecosystems.
Aluminium is a common element in the Earth’s crust and under neutral pH conditions forms a white, non-toxic solid susbstance. However, under acidic (low) or basic (high) pH, aluminium dissolves and becomes toxic to aquatic animals. Fish are the most susceptible group to aluminiuim toxicity effects, with first clogging of the gills and then disruption of their ability to regulate water content in the body occuring as pH decreases.
-Ecotoxicological Review of Alum Applications to the Rotorua Lakes
When determining a dosage for freshwater lakes, consideration must be given to the ability of the water body to resist/offset any change to pH, the ‘buffering’ capability.
In addition, eutrophic systems often experience photosynthetic driven alkaline pH shifts, resulting in Al solubilisation and the formation of the toxic Al species Al(OH)4-. -IBID
A eutrophic system is one where excessive plant growth occurs due to increased availablity of sunlight, carbon dioxide or nutrient fertilisers. High levels of nutrient have previously been recorded in Rarotonga where streams discharge to the lagoon, and algal bloom has been observed both in the streams and lagoon.
A difference between streams and lakes regarding toxicity, is that the settling of aluminium floc to the lake floor can isolate it from transitory changes in pH. In Rarotonga, where streams can run-dry, the periodic heavy rainfall can remobilise silt, and would likewise resurface any aluminium floc that might form in the streambed when aluminium wastewater is discharged from the water treatment facilities.
Current research suggests that the risks of AI bioaccumulation are relatively low. … Increased tissue concentrations of AI have been reported in koura (Paranephrops plonifrons) and common bully (Gobiomorphus cotidianus) in the Utuhina Stream but no
toxicological effects have been observed. …It should be noted that chronic effects of AI exposure are not as well studied and a cautious approach is recommended. -IBID
Sediment Accumulation of Aluminium Deposition and Potential Release
There is a notable absence in the published literature of the long-term fate and effects of anthropogenic AI in sediments. Despite alum first being used for lake restoration in Europe from 1968 (lake Umgsjon) … no applied or theoretical research has been published examining the effects of high AI deposition over sustained time periods (i.e. >10 years). This includes both the ultimate fate of aluminium in sediments and effects on biota.
Without surveying the valley streams and waterways prior to chemical use it will be difficult to track or attribute impacts.
Bodies of freshwater in the Cook Islands are extremely limited, with no large lakes or rivers, only wetlands, streams and a few small freshwater lakes present. Freshwater biodiversity is therefore extremely limited. The Cook Islands National Biodiversity Strategy and Action Plan (NBSAP) lists only nine native and four introduced fish species, two native and three introduced gastropods, and six native and one introduced crustacean. Cook Islands 4th National Report to the Convention on Biological Diversity (2011), National Environment Service.
Potential impacts on plants and insect life should also be further researched.
NZ: Freshwater Management
As a regional and regulatory reference-point, the New Zealand policy statement on the management of freshwater ecosystems may help to identify impact areas requiring monitoring:
In a healthy freshwater ecosystem ecological processes are maintained, there is a range and diversity of indigenous flora and fauna, and there is resilience to change.
Matters to take into account for a healthy freshwater ecosystem include the management of
adverse effects on flora and fauna of contaminants, changes in freshwater chemistry, excessive
nutrients, algal blooms, high sediment levels, high temperatures, low oxygen, invasive species,
and changes in flow regime. Other matters to take into account include the essential habitat
needs of flora and fauna and the connections between water bodies.
New Zealand: National Policy Statement for Freshwater Management 2014 (amended 2017)
Impacts of water treatment chemicals on the lagoon, reef and ocean require research specific to Rarotonga. International research indicates linkages between freshwater quality, chemical pollution, and reef health.
“Citing climate change as the exclusive cause of coral reef demise worldwide misses the critical point that water quality plays a role, too. While there is little that communities living near coral reefs can do to stop global warming, there is a lot they can do to reduce nitrogen runoff… the fight to preserve coral reefs requires local, not just global, action.” 15 July 2019: Thirty years of unique data reveal what’s really killing coral reefs. Science Daily. Accessed 29 July 2019.
Liability for Environmental Incidents
Consideration of liability for environmental damage involves analysis of whether the Government has a “power of control” over the work of contractors such that the Government is vicariously liable:
The test [to prove vicarious liability] involves:
a right to direct the subcontractor in circumstances where the right is capable of exercise and is, or is likely to be effective; and
actual control of a course of action taken by the independent subcontractor; ie, control over the way in which the tasks are to be performed or how they are to be carried out.
In other words, it is critical whether the Government controls how work is carried out by the consultancy or contracting firm.
Comissioning of the Te Mato Vai Water Treatment System
The Cook Islands Government announced commissioning in a double-page spread appearing in the Cook Islands News, 30 November 2019.
The Cook Islands Government has instructed the Te Mato Vai Stage 2 contractor McConnell Dowell to begin commissioning the new intake water supply systems. Currently the public water supply is still connected to the old intake infrastructure. Improved water will soon flow through new water supply system. Cook Islands Government Release in Cook Islands News, 30 Nov 2019.
If the wording seems awkward, it’s likely as result of the vicarious liability issue outlined above; to make clear that the contractor has been directly instructed by government to proceed (and is carrying out works to the specification of the national water supply standards). It is now the government that assumes all responsibility for environmental damage that might occur as a result of the shock-chlorination.
According to the To Tatou Vai Public Notice appearing in the same paper:
Matavera Intake Shut Down The contractor is undertaking commissioning works for Matavera intake and may require a shut down on the following days Monday 2 December, 8am to 1PM… -IBID
Community group Te Vai Ora Maori protested the commissioning the morning the work was scheduled to commence.
Takuvaine Stream Die-Off: Dec 2019
The following Wednesday a further notice was published; and the same week letters were delivered to Landowners to notify that the Takuvaine WTP was to be commissioned Fri 13 Dec.
Landowners visiting the plant on Monday 16 Dec saw operations staff in personal protection equipment dosing the settlement tank with chlorine solution.
The Landowners had previously been advised that chlorinated water was to be held in the settlement tank for 24 hours and then drained through the treatment plant network to the lower water storage tank, where it would remain for 3-6 weeks to allow the chlorine to disappate / be reduced to non-toxic levels. Instead it appears that chemical water was partially or entirely discharged into the Takuvaine stream.
20 Dec 2020: Report submitted to authorities requesting formal investigation into potential environmental incident.
24 Dec 2019: Although no investigation has been conducted by the National Environment Service; no formal response tended to the complainant; and despite the eyewitness accounts; the Secretary of Finance issues statements to local and international media: “…the complainants were wrong. There was no evidence to back such claims, he said, with no photos of the supposedly dead fish and eels the landowners say had died.”
27 April 2020: An independent expert review of the Te Mato Vai water treatment system was commissioned by the Cook Islands Ministry of Justice in Feb-Mar 2020. As part of a walk-through of the waterworks, a potential engineering fault was identified: when the settlement tank is full, streamwater will flow through the Inlet Chamber (where PACl is dosed) and then overflow to the stream. During disinfection, (if left unattended), the design of the system appears to allow for high-dose chlorinated water to overflow into the stream. If this interpretation is correct, it this would account for the residents’s observations. The Expert description of the ‘fault’ and the response from GHD was requested 15 April 2020 but has not been answered as at 28 June 2020.
Emptying the Settlement Tank (enlargement added) from ‘Information to support approval to commission Te Mato Vai Stage 2’.
GHD, Nov 2019. The diagram suggests that operator inattention to the process of disinfecting the settlement tanks could result in chemically-treated water overflowing to the stream. 1. Raw water from the intake (stream) is piped to the Inlet Mixing Chamber. 2. (When operational) the PACl line feeds a solution of polyaluminum chloride into the Mixing Chamber. 3. When the Settling Tank is full; the Overflow returns water from the Mixing Chamber back to Stream (dosing of PACl will also stop when the tank is full).
25 June 2020: In a Te Mato Vai photo opportunity staged to coincide with the June session of Parliament it was revealed that the backwash (PACl wastewater) storage pond required reconstruction after it was damaged in a storm event. If the plant had been operational, the contents of the pond would have overflowed into the Takuvaine stream. PMU Response 22 July: A culvert outside of the Takuvaine Stage 2 construction site became blocked, causing an overflow of water to run over the road, down past the settling tank to the scour ponds… causing some minor erosion of the scour pond embankments. [Remediation] reshaping of the ground profile upstream and around the culvert area to divert any overflow back into the stream. A concrete ford crossing is also being constructed on top of the culverts to further protect the culvert and access road from future extreme rainfall events.
Chemicals have been proposed for the ongoing treatment of Rarotonga’s water supply for the purpose of coagulation and disinfection. Estimated value of coagulation and disinfection chemical contract: $350-500k / year.
Pool Treatment 101: Introduction To Chlorine Sanitizing
The American Chemistry Council Parts per million (ppm). Measurement that indicates the parts of a substance, such as chlorine, by weight in relation to one million parts by volume of pool water. A rule of thumb to follow to maintain good water quality in pools is to keep free available chlorine levels between 2.0 and 4.0 ppm.
Fish community surveys and biomonitoring
in selected Rotorua Streams. M Landman et al, Scion. 2008. It is
suggested that the initial decline in fish abundance during the first year of [continous] alum dosing may have been linked to avoidance of exposure to increased Al, reduced pH or a combination of the two, followed by subsequent acclimatisation and recovery of the population.
Aquatic Macroinvertebrates: Biological Indicators of Stream Health. University of Kentucky.
Examples of aquatic macroinvertebrates include insects, worms, snails, mollusks, and crustaceans… macroinvertebrates are an integral part of the food chain. Without these creatures, a stream’s entire aquatic food web would collapse. Many macro-invertebrates feed on organic material such as leaves and algae.
Antidepressant pollution alters crayfish behavior — Impacting stream ecosystems. June 2021.
Just two weeks of citalopram exposure caused changes in crayfish behavior, with the potential to disrupt stream ecosystem processes like nutrient cycling, oxygen levels, and algal growth.
Crayfish are a keystone species in streams, where they eat invertebrates, break down leaf litter, and cycle nutrients. They are stress-tolerant and can become abundant in urban waterways. These freshwaters are prone to receiving pharmaceutical pollution from sewer overflows, leaky septic tanks, and treated wastewater effluent that contains pharmaceuticals.
12 Nov 2019: Cooks water quality campaigners dismissed as extremists. RNZ News. The Cook Islands Deputy Prime Minister is characterising opponents to the use of chlorine in Rarotonga’s new water system as uninformed extremists.
RNZ: Have you had an environmental impact assessment done of the use of chlorine?
MB: I think that’s a question that should be posed to the environment service, I’m not aware of the full procedures that are being followed, but the government is committed to following proper procedure in terms of ensuring that clean drinking-water to the public on Rarotonga.
RNZ: The reports I get from environmental groups is that there hasn’t been any environmental impact assessment done.
MB: Yes, I’m not sure that's an accurate statement, but we’ll need to verify that.… I’m finding it difficult that the extreme views held by certain people should be used to determine the best possible drinking-water system for the people of the Cook Islands, the people of Rarotonga.
22 Nov 2019: Prawn numbers decline — claim. Cook Islands News.
“Below the construction site, there was a marked decrease in prawn numbers. Above the discharge pipe — plenty of prawns,” he says, in a letter to Cook Islands News. “A local who fishes the area told me of a similar incident in Avana; and that he had been removing carcasses from the stream.” Kirkwood said government’s Project Management Unit had assured him no chemicals had been used, but had declined to supply workplace records to show whether something else might have contaminated the stream. “Nothing has been done to prevent damage to the other intake streams.”
24 Dec 2019: Chemicals claim wrong: Henderson . Cook Islands News. Government has refuted claims that disinfected water containing chemicals has been released into the Takuvaine stream. … financial secretary Garth Henderson assured the public, especially the landowners up at the Takuvaine intake, that “no calcium hypochlorite has been disposed into the stream”.
24 Dec 2019: Another stoush in Cook Islands over chlorine in water. RNZ News. [Landowner Tere Carr] “What we suspect happened last Monday is that the chlorinated water from one of the tanks was released into the stream that runs past where the works are located. So there’s real concern from the landowners on the Takuvaine Intake that this could have happened. As a result there was evidence of some of the animals in the stream having been affected and having died.” However, Secretary of Finance Garth Henderson, speaking for the government, said the complainants were wrong. There was no evidence to back such claims, he said, with no photos of the supposedly dead fish and eels the landowners say had died.
23 May 2020: Andy Kirkwood: Water treatment: Don’t be hasty. Cook Islands News.
The Government intends to proceed with a separate six-month PACl trial, despite not having a permit to do so. The Government claims the trial is necessary to inform the environmental impact assessment. This claim is not supported by the GHD technical documentation, the Court-expert assessment, or the opinion of the consultancy firm preparing the To Tatou Vai environmental impact assessment submission. The Government’s claim requiring a trial is necessary, is a fiction.
25 Jun 2020: Turning on the taps Katrina Tanirau, Cook Islands News. Authorities acknowledge they need to be as transparent as the water they plan to pipe into people’s homes in Rarotonga.…
Storm damage to the main water storage pond meant it had to be reconstructed, and that delayed the project.
4 July 2020: Pipe gushes despite pleas. Melina Etches, Cook Islands News. A large high-pressure water pipe has burst at the Turangi intake road and is being held together by tyre tubes to limit the spill. With the shortage of water issue experienced on the island, a concerned neighbour was upset at the poor effort to fix the problem. “It’s been like this for at least two months, during this time of drought…”
8 Aug 2020: Floods knock out key water mains. Katrina Tanirau, Cook Islands News. Severe damage to aged water mains up the Avana and Turangi valleys is cited as evidence of the urgent need to switch over to the new network.
24 Aug 2020: Activists claim Cook Islands Govt set to illegally use chemicals in water. RNZ.
The Cook Islands News reported the group alleged last month, in a complaint to the National Environment Service, that the government was dosing the water supply with a chemical coagulant without a proper permit.
The group said its complaint is not about the science of water treatment, but about the “regulatory process”.
Earlier this month To Tatou Vai, the authority being set up to run the scheme, wrote to landowners saying it was about to start a six month trial using the coagulant.
4 / 22 Dec 2020 Te Mato Vai Aquatic Ecology Report Released. GHD.
Earlier this year a field study on the 10 streams where water intakes have been upgraded was conducted. … Alongside the field study a report that described the existing aquatic ecological values of the 10 intake and discharge sites was produced. As part of this study, we assessed the potential impacts of the water treatment plant operations…
8 Dec 2020 Government’s ecological report challenged. Cook Islands News.
A desktop review relies on published reports. The consultants did not conduct any fieldwork on the sensitivity of Rarotonga’s freshwater ecosystems to pollution.
ADB Country Partnership Strategy Cook Islands 2008-2012. Jun 2008. Behavioral changes (particularly attitudes towards cost recovery) will be needed to establish efficient service delivery (especially in water, sanitation and waste management) to ensure that reformed agencies are able to operate efficiently. Sustained government commitment to the objectives will be a challenge.
Agriculture Field Reports Feb 2016. Ministry of Agriculture.
Suggestions by the Ministry of Agriculture, during
Stakeholders meetings in 2014 and 2015 for this
current [water distribution] system to be left for Agriculture and Livestock
use in support of Agriculture production and Food
Security. The response from the Government (i.e.
Mato Vai Officials): challenges in the
lost of water flow in these old water mains due to
leakages; expense. The Ministry of Agriculture strongly
believes that the idea and suggestions to retain the
current water system for Agriculture and Livestock use
is a very worthwhile venture especially for our Food
Security and wellbeing in combating Climate Change,
Prolong Drought due to shifting of global rain patterns,
etc. Involved: Sam Napa, William Wigmore, Patrick Arioka, Matairangi Purea. Includes Japanese Designed Water Map Of The Water Systems In Rarotonga 1991.
Progressed to Green Climate Fund Project Idea; under Food Security (2016-17).
Terms Of Reference:
For Supply Of Water Treatment Chemicals. To Tatou Vai Ltd. May 2019.
1.2(iii) Quantities required are indicative only at this stage, represented as an annualised total as below:
A. Poly Aluminum Chloride: 75-100 Tonnes
B. Calcium Hypochlorite: 8-10 Tonnes 1.5 Estimated Value of the Works
The Principal has estimated the value of the works at between $NZD 350,000.00 and $NZD 500,000.00.
Information Pack: Stage 2 Commissioning. GHD. Nov 2019. “Dear Landowners,
This information pack has been prepared to support your decision about whether you approve the Cook Islands Government’s (CIG) recent instruction to the PMU to begin commissioning the new intake water supply systems, known as Te Mato Vai Stage 2.”
Environment Act 2003. PacLII.
S.36 (1) No person shall undertake any activity which causes or is likely to cause significant environmental impacts except in accordance with a project permit issued under this section.
(3) Every application for a project permit shall be submitted to the Service and shall include an environment impact assessment…
(b) the proposed action to mitigate adverse environmental effects and the proposed plan to monitor environmental impact arising out of the project;
(5) The Service shall undertake public consultation for the issuance of the project permit and in so doing-
(a) publish details of the project in such a manner that these become accessible to the affected public;
(13) For the purposes of subsection (1), any designation, orissue or re-issue of approval of any land (whether by a Minister or any other public officer or authority, and whether under this or any other Act) for the disposal of any kind of waste is deemed to be an activity that is likely to
cause significant environmental impacts.
Public Health Act 2004. PacLII. Material including sludge or other by products from water treatment plants is ‘Hazardous waste’. Section 54(2)(d) “prohibits hazardous waste to be directly or indirectly deposited or discharged, or to seep, into a waterway”.
Official Information Act 2008, 2009. PacLII. 11.(3) If the person making the request asks that his request be treated as urgent, he shall give his reasons for seeking the information urgently. 13. Transfer of requests – Where – …
(a) a request in accordance with section 11 of this Act is made to a Ministry or Minister of the Crown or organisation; and
(b) the information to which the request relates —
(i) is not held by the Ministry or Minister of the Crown or organisation but is believed by the person dealing with the request to be held by another Ministry or Minister of the Crown or organisation; or …
the Ministry or Minister of the Crown or organisation to which the request is made shall promptly, and in any case not later than 10 working days after the day on which the request is received, transfer the request to the other Ministry or Minister of the Crown or organisation, and inform the person making the request accordingly. 14. Decisions on requests – (1) Subject to this Act, the Ministry or Minister of the Crown or organisation to whom a request is made in accordance with section 11 or is transferred in accordance section 13 of this Act shall, as soon as reasonably practicable, and in any case not later than 20 working days after the day on which the request is received by that Ministry or Minister of the Crown or organisation,…